Home of the National Fire Sprinkler Association
The storage of Group A plastic on racks is one of the most challenging fire situations that fire sprinklers can experience. These storage arrangements can promote a severe fire condition which may include a rapid spread of fire with a high rate of heat release. Chapter 17 in NFPA 13 titled “Protection of Rack Storage of Plastic and Rubber Commodities” spells out the acceptable protection options for this extreme fire risk. Chapter 17 gives the layout technician many options including the use of Standard Spray Sprinklers (CMDA), Control Mode Specific Application sprinklers (CMSA), Early Suppression Fast Response sprinklers (ESFR) and in-rack sprinklers.
This presentation will outline the different acceptable protection criteria and options found in Chapter 17. A thorough understanding of the requirements of this chapter will help the layout technician to choose the most appropriate protection for this challenging storage arrangement.
12/6/2016 » 12/8/2016Tulsa, OK
12/7/2016Columbia-Willamette Chapter Meeting
12/8/2016Puget Sound Chapter Meeting
12/13/2016 » 12/15/2016Bellingham, WA
12/20/2016Technical Tuesday-Inspecting Storage Occupancies
"To protect lives and property from fire through the widespread acceptance of the fire sprinkler concept"-NFSA Mission Statement
Phone: (845) 878-4200
Fax: (845) 878-4215
MD Office - 514 Progress Drive Suite A Linthicum Heights, MD 21090
NY Office - 40 Jon Barrett Road Patterson, NY 12563